Cabinet type FM200 gas suppression system is a portable fire-fighting equipment with automatic fire detection, alarm and fire extinguishing. Its performance is excellent, and its control part can be connected with the fire control center.
The gas extinguishing agent storage cylinder of cabinet type FM200 gas suppression system is packaged into a fire extinguishing cabinet, which is usually placed in a protection area. When there is a fire, the gas suppression system doesn’t need to go through many pipelines, and it can be directly sprayed in the protection area.
What Consists in System
Cabinet type FM200 gas suppression system includes storage cylinders, starting devices, main relief valves, pressure gauges, cabinets, pressure signal devices, short spray pipes, nozzles, and FM200 fire extinguishing agents.
Cabinet type FM200 gas suppression system is suitable for data centers, libraries, archives, valuables warehouses, power stations (transformer rooms), telecommunications centers, clean workshops and other important places.
Advantages and Disadvantages of Manifold Type and Cabinet Type FM200 Gas Suppression System
1.Manifold type system sprays the agent through the pipe network, and the nozzles are evenly distributed, so the spraying is even and the fire extinguishing effect is good, while the cabinet type system network generally sprays directly from the cabinet nozzles, and the spraying is not even enough.
2.Manifold type FM200 gas suppression system should have a separate cylinder room and pipe network, while cabinet type system doesn’t need pipe network. If there is only one area that needs to be protected, the cost of the manifold type system will be higher economically.
3.If there are many protection areas, the manifold type system can use the same system to protect different areas, targeted spraying. and the cabinet type system requires separate cylinders and fire extinguishing agents for each protection area. Under this circumstance, the price of the cabinet type system is relatively high.
4.The cylinders of manifold type system are in cylinder room. Because of the long distance, high pressure is required, generally is 4.2MPa.
5.The cylinders of cabinet type system are in protection area. The pressure should not be too high, generally is 2.5MPa.
ASENWARE provides cabinet type FM200 gas suppression system for customers, spraying the extinguishing gas to the protection area quickly to protect the safety of people and assets.